Products >> Level Switches For Solids >> Chute | Diaphragm | Boot | Level Switch
Boot level change is applicable to detect the level in the bucket alligator boot & similar small hopers and ducts.
JayceeTech is leading maunufacter of Chute level switch, boot, diaphragm level switch in India. We offer predominant Diaphragm Level Switch that is made up from quality material with with perfect finishing. Known for its impeccable highlights, Diaphragm Level Switch is very popular among our clients. Boot level switch is applicable to detect the level in the bucket alligator boot & similar small hopers and ducts.
We always want to be one step ahead in order to furnish the best technological equipment to the world. That is why we try to inculcate more and more features in our products. Points related to products that make a difference in our industry:
JayceeTech is leading manufacturer of Chute level switch, boot and diaphragm level switch in India. We offer Diaphragm/Boot Level Switch is applicable to detect the level in the Bucket Elevator boot & similar small hoppers and ducts.
Our Chute Level Switch is used for indicating, controlling, the level of granulated or powdered dry materials through the plant control system. It is applied to all free-flowing grains and powders but used for the solid items only.
Our chute level switches hasnormal sensitivity in the range of 100 to 400gm depending upon the model. The ambient temperature is 60 Deg C. and special design suitable up to 150 Deg C. The main body of these switches is designed of cast aluminium along with the use of polymer switch housing. It is suitable for free flowing powder and grains like food grains.
|Normal sensitivity||200 gm / 400 gm|
|Diaphragm Membrane material||Nitrial Rubber / SS|
|Ambient temperature||60 Deg Micro switch|
|Contacts||15 Amp, 230 V AC, Potential free|
|Cable Gland||PG 11|
|Main body||Cast Aluminium|
|Switching Housing||Polymer for SS type|
The JAYCEEBOOT level switch is used for indicating, controlling, and regulating the level of granulated or powdered dry materials with a grain diameter up to 15mm and a density of 0,3 to 2,5 g/cm3, flowing through a silo, hopper or chute.
The device must be mounted so that the diaphragm membrane is exposed to the product whose level should be controlled, in such a way that the product, can press the diaphragm.
The material weight presses the diaphragm which is adjusted with the micro switch through a flexible mechanism. A liver attached to the diaphragm transfers the pressure to the micro switch which changes the contact.
When the material recedes the diaphragm comes back to its normal position and the micro switch again changes the contact.